RT300,CANopen remote I/O, DI*16/DO*16 relay
CANopen is one of the mainstream industrial fieldbus now. SOFTLINK CANopen slave modules realize quick connection to CANopen network, collecting field signals and communicating with master, to reliably complete its control on machinery and equipments.
In order to meet the needs of machine manufacturers and users, distributed automation architecture is used more and more in a variety of occasions, and implementation and functionality comparable to a centralized system. RT13X series IO is a completely new modular input and output device sit made possible through the bus utilization master to manage the design of automation equipment for distribution in the scene of the switch input and output signals and analog input and output signals, connected to the control system through the rich industrial fieldbus the use of IO communication network IO distribution to multiple locations away from the processor, try closer to the sensors and actuators used in distributed control systems flexible and plays a prominent role.
In the design of modern automation system, the application of industrial fieldbus impact automation. Why is traditional centralized control structure gradually replaced by distributed intelligent devices? Because it is cost-saving and system –optimizing.
Remote I/O: Design of 2 layers of terminal makes it easier to connect Optimized wiring design in the module makes cabling easier
In automation equipment away from the master controller, long distance cable can result in the attenuation and interference of control signal. Such problem can be avoided in the distributed I/O system. System processor located in master control room I/Os distributed in each control position RT13x series I/O exchange data with master controller via industrial field bus.
|Type||Digital I/O module|
|Number of Input||16|
|Nominal Input Voltage||24VDC (-15%/+20%)|
|"1" Signal Voltage||15~30VDC, 7mA|
|"0" Signal Voltage||0~5VDC|
|Port Protect||Impact over voltage protection|
|Number of Output||16|
|Nominal Output Voltage||30 V DC/250V AC|
|"1" Signal Voltage||Dry contact short circuit|
|"0" Signal Voltage||Dry contact open circuit|
|Max. Output Current (per Ch.)||1 A|
|Short Circuit Current (per Ch.)||2 A|
|Max. Output Current (Total.)||16A|
|Supply Voltage||24VDC (-15%/+20%)|
|Electrical Isolation (Bus/Field protential)||AC 500V|
|Bus Connector||D-Sub9 Female|
|Communication Rate||10kbps~1Mbps Config by 3-bit dial switch|
|Address Config||00 ~ 99 (Config by 2-bit dial switch)|
|Fixed Method||DIN rail (TS35)|
|LED Indicate||PWR:Green;ERR:Red;DE,Data exchange:Orange;Digital I/O:Green|